Site assessments are one of TechSite’s core offerings and a valuable service for IT and facilities personnel to gain a better understanding of their critical data center infrastructure. In addition to evaluating and documenting the critical electrical and mechanical elements of a data center, observations and recommendations for the fire detection and suppression systems are often included with one of these assessments. Many different approaches have been taken throughout the industry to protect the critical IT assets from fire with varying degrees of design complexity, including the use of pre-action sprinkler systems.
Pre-Action Sprinkler Systems in a Data Center
Conventional wet pipe, water based sprinkler systems are never preferred in the data center due to the inherent risks associated with a potential leak and/or damaged sprinkler head accidentally discharging water onto the IT equipment. A pre-action system however, is a water based system that is not only considered acceptable, but is a component of TechSite’s standard recommendations for protecting a data center from a fire. The following article will provide a quick summary of a pre-action system, several configurations available, a summary of operation and the reasoning behind installing such a system in a data center.
A pre-action sprinkler system is different than a wet pipe system typically found in commercial applications. Instead of water, the pipes are normally filled with compressed air or nitrogen and water is only released to the space following a combination of events that would indicate a fire is present in the area(s) being protected. A pre-action system can be used in conjunction with a clean agent gas suppression system or as the single form of fire protection but requires a supplemental electric fire detection system to be in place. A pre-action system includes a specialized control valve that is configured to remain closed until absolutely necessary to delay a discharge of water onto critical IT equipment. This type of system is highly desirable in a data center due to the fact that a water discharge, equipment emergency power off (EPO) and the associated cleanup is often more costly to a business than the fire itself.
Two types of pre-action systems are most common (Single and Double Interlock) and are similarly designed with the primary differences being the valve that is installed and the number of events necessary prior to water being released into the pipe. Both a single and double interlock system require two events to occur before water is discharged to the protected area.
Single Interlock System
Double Interlock System
Reasons for Installing a Pre-Action Sprinkler System in Your Data Center
Installation and retrofit costs for installing a pre-action system are higher than a standard wet pipe system. There is also additional maintenance, training and documentation over a standard wet sprinkler system due to added complexity. Ultimately, a pre-action sprinkler system provides one of the safest forms of data center protection when contemplating a water-based system.